Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Backflow Damper Leakage on a Non-Operating MicroTurbine on a Common Exhaust Duct
Original File Name Searched: SB0087A_Backflow_Damper_Leakage_on_Non-op_MT_on_Common_Exh_Duct.pdf | Google It | Yahoo | Bing
Text | Backflow Damper Leakage on a Non-Operating MicroTurbine on a Common Exhaust Duct | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Fax: (818) 734-5320 • Web: www.capstoneturbine.com
Service Bulletin SB0087
Date: From: Subject:
Capstone Technical Support
Backflow Damper Leakage on a Non-Operating MicroTurbine on a Common Exhaust Duct
All Capstone MicroTurbine systems operating with a common exhaust duct.
Only Capstone Authorized Serviced Providers (ASPs) should open the MicroTurbine and other equipment connected to the MicroTurbine. The systems can include multiple sources of power. The fuel used by the MicroTurbine is flammable and explosive. Keep flames, cigarettes, sparks, and electrical arc-producing equipment away from the MicroTurbine. Observe and adhere to the Safety Instructions contained within the MicroTurbine documentation.
This service bulletin is intended to notify Authorized Service Providers of possible component damage relating to MicroTurbine systems sharing a common exhaust duct with Capstone supplied Backflow Dampers installed.
Per previously issued Capstone Service Bulletin SB0073, all MicroTurbines on a common exhaust duct must run simultaneously. In addition, Capstone requires a wiring interlock mechanism to be installed between MicroTurbine systems to stop the operation of all MicroTurbines if any individual MicroTurbine ceases operation. This interlock is required unless a Capstone-supplied exhaust Backflow Damper is properly installed in the individual exhaust ducts of each MicroTurbine feeding the common exhaust duct.
When Capstone Backflow Dampers are used, additional measures are recommended to protect non-operational MicroTurbines. Since Capstone Backflow Dampers do not provide a bubble-tight seal, installations with two or more MicroTurbine systems sharing a common exhaust duct will allow a small leakage of hot exhaust into the non-operating unit. The water content in this leakage exhaust may condense in the non-operating engine recuperator and power head, potentially causing damage to the engine.
450075 Rev A (August 2008) Page 1 of 3
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Image | Backflow Damper Leakage on a Non-Operating MicroTurbine on a Common Exhaust Duct
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: email@example.com