Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Capstone Technical Support HRM Inspection
Original File Name Searched: SB0092A_HRM_Inspection.pdf | Google It | Yahoo | Bing
Text | Capstone Technical Support HRM Inspection | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Fax: (818) 734-5320 • Web: www.capstoneturbine.com
Service Bulletin SB0092
Date: From: Subject:
Capstone Technical Support HRM Inspection
All Capstone Heat Recovery Modules (HRMs) shipped between January 2007 and August 2008, either as part of a C65 ICHP MicroTurbine or as a field upgrade to a C60/C65 MicroTurbine, which are in inventory or not yet commissioned.
Only Capstone Authorized Serviced Providers (ASPs) should open the MicroTurbine and other equipment connected to the MicroTurbine. The systems can include multiple sources of power. The fuel used by the MicroTurbine is flammable and explosive. Keep flames, cigarettes, sparks, and electrical arc-producing equipment away from the MicroTurbine. Observe and adhere to the Safety Instructions contained within the MicroTurbine documentation.
This service bulletin is intended to notify Authorized Service Providers that HRMs shipped between January 2007 and August 2008, either as part of a C65 ICHP MicroTurbine or as a field upgrade to a C60/C65 MicroTurbine, which are in inventory or have not yet been commissioned, require inspection per the instructions provided below. There is potential that a protective cardboard insertion sleeve inside the unit was not removed prior to shipment. Presence of this cardboard insertion sleeve can cause smoking and/or fire in the unit. Units must be inspected for presence of this cardboard insertion sleeve prior to operation.
If your unit has run for an hour or longer, and the HRM did not exhibit these symptoms, you do not need to perform this inspection.
450083 Rev A (August 2008) Page 1 of 7
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Failure to perform this inspection prior to operating the unit may result in smoking and/or fire in the unit, creating a potential for serious injury to personnel as well as damage to the unit.
Image | Capstone Technical Support HRM Inspection
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: firstname.lastname@example.org