Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Connector Change on TET Themocouple Cable
Original File Name Searched: SN0019_C30_C65_TET_Connector_Retrofit.pdf | Google It | Yahoo | Bing
Text | Connector Change on TET Themocouple Cable | 001
Capstone Turbine Corporation 21211 Nordhoff Street Chatsworth CA 91311 USA Telephone: (818) 734-5300 Fax: (818) 734-5320 Website: www.capstoneturbine.com
Service Notice SN0019
Date: From: Subject:
Capstone Model C30 and Model C65 MicroTurbines approaching a 20,000 hour service interval, or those requiring replacement of a TET thermocouple or engine.
The TET Sensor connector and engine harness connector have changed from a DB9 type (see Figure 1) to Type K mini connectors (see Figure 2). This change is effective on new TET thermocouples and new engines as of February 2009. This change requires purchase of a field retrofit kit (610228-100), which provides the necessary parts and work instructions (440177) to retrofit older engine harness connectors to match the new TET sensor connectors.
Capstone Technical Support
Connector Change on TET Thermocouple Cable
Figure 1 – TET Sensor with DB9 Connector
Figure 2 – TET Sensor with Type K Mini Connectors
450079 Rev A (February 2009)
Page 1 of 2
Capstone reserves the right to change or modify, without notice, the design, specifications, and/or contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Image | Connector Change on TET Themocouple Cable
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: email@example.com