Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Dual Mode Controller Relay Update Capstone Model 330 MicroTurbine
Original File Name Searched: SB0024_DMC_Relay_Update_C30.pdf | Google It | Yahoo | Bing
Text | Dual Mode Controller Relay Update Capstone Model 330 MicroTurbine | 001
Date: From: Subject:
Capstone Customer Service
Dual Mode Controller Relay Update Capstone Model 330 MicroTurbine
Capstone Customer Service Toll Free Phone: (877) 282-8966 E-mail: firstname.lastname@example.org Phone: (818) 734-5325 • Fax: (818) 734-1070
Be sure to read these instructions when using a Dual Mode Controller (DMC) with the Capstone Model 330 MicroTurbine.
This document provides information for adding a relay to the DMC used with the Capstone Model 330 MicroTurbine.
All Dual Mode Controllers with part numbers: 509921 and 510594 through 510600.
It is possible that a failure of the electronic controllers inside the MicroTurbine (or the master MicroTurbine in a MultiPac) can prohibit the protective loads from being energized by the utility power. Servicing, software upgrade, or rebooting the system may also cause the protective loads to lose power.
The addition of a relay inside the DMC solves this problem by allowing the protective loads to be energized by the utility power through the DMC, regardless of the state of the MicroTurbine.
512772-001 (Sept 2001) Page 1 of 12 Service Bulletin SB0024.
Capstone Turbine Corporation reserves the right to change or modify without notice the design, the equipment specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Image | Dual Mode Controller Relay Update Capstone Model 330 MicroTurbine
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: email@example.com