Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Inspected Foil Bearing RFC Heat Exchanger
Original File Name Searched: SB0039_Inspect_Foil_Bearing_RFC_Heat_Exchanger.pdf | Google It | Yahoo | Bing
Text | Inspected Foil Bearing RFC Heat Exchanger | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Facsimile: (818) 734-5320 • Website: www.microturbine.com
Service Bulletin SB0039
Date: From: Subject:
All Low Pressure Foil Bearing RFC Model C30 MicroTurbine systems and retrofit kits supplied by Capstone Turbine Corporation® before July 31, 2002.
Only Capstone Authorized Service Providers (ASP’s) should open the MicroTurbine and other equipment connected to the MicroTurbine. The systems can include multiple sources of power. Observe and adhere to the Safety Instructions contained within the MicroTurbine manuals.
Damage may occur to the heat exchanger during shipping or installation. This may result in fuel leaks, which can lead to safety issues or further component damage. Systems should be inspected to ensure that no cracks or visible damage is present at the heat exchanger.
If any cracks or visible damage is found, the heat exchanger must be replaced immediately. If no cracks or visible damage is found, the heat exchanger should be replaced at the next scheduled service visit.
To ensure reliability, an upgrade kit is available for all Low Pressure Foil Bearing RFC Model C30 MicroTurbine Systems and Retrofit Kits, containing an intercooler and bracket assembly.
It is the responsibility of Capstone to provide this Service Bulletin to Authorized Service Providers.
It is the responsibility of Capstone to make available the upgrade kit to Authorized Service Providers for the resolution of issues related to fielded MicroTurbine systems.
After completion of the task, it is the responsibility of the Authorized Service Provider to provide Capstone with a Field Service Report.
If you have additional questions, please contact Capstone at:
450003-001 Rev B (October 2003) Page 1 of 1
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Capstone Technical Support
Inspect Foil Bearing RFC Heat Exchanger
This revision of the Service Bulletin SB0039 supersedes the Revision A document that was released July 2002.
Capstone Technical Support
Toll Free Telephone: (877) 282-8966 Service Telephone: (818) 407-3600 Facsimile: (818) 734-1080
Capstone Technical Support (Japan)
Service Telephone: (818) 407-3700 Facsimile: (818) 734-1080
Image | Inspected Foil Bearing RFC Heat Exchanger
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: email@example.com