Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Model C30 Software Version 4.93 Release Notes
Original File Name Searched: SB0052_ModelC30SoftwareVersion493 Release Notes.pdf | Google It | Yahoo | Bing
Text | Model C30 Software Version 4.93 Release Notes | 001
Service Bulletin SB0052
All Capstone Model C30 Stationary MicroTurbine Systems.
Version 4.93 software has been released to support the Model C30 MicroTurbine systems. This release offers the following major changes:
1. System Improvements:
♦ A new display item has been added for setting and displaying user’s power demand (PWRDMD). This value is different from the Stored Power Demand (PWRDST) value that was already being displayed.
♦ Allows MicroTurbines without a battery (GC-only units) to be compatible with a Capstone Power Server.
♦ Allows user to enable/disable the daylight savings time feature on the real-time clock.
♦ Allows a MultiPac Disabled MicroTurbine (number greater than 1) to accept serial commands from MicroTurbine Number 1.
♦ Changed the default settings of the UCB Output Relays to be set for the new function “Unused” and configured to be “Active Open”.
♦ Allows a MicroTurbine to auto-restart after a 5000 Fuel Subsystem fault with SPV PIC software version 2.14 and higher. The SPV Part Numbers shipped with this software are:
503044-103 509224-202 513321-101
2. Liquid Fuel Systems:
503044-202 509224-102 511098-102 512035-102 513321-201
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Facsimile: (818) 734-5320 • Website: www.microturbine.com
Capstone Technical Support
Model C30 Software Version 4.93 Release Notes
♦ Injector #2 clogged fault (16019 LF INJ2 CLGD) and injector #3 clogged fault (16020 LF INJ3 CLGD) are treated as warning faults and the system is allowed to run with the good injectors. However, if both injectors #2 and #3 are clogged (16021 LF MULTI INJ CLGD), or if injector #1 is clogged (16018 LF INJ1 CLGD), the system will always transition to the Fault state.
♦ A new fatal fault “5022 NO AIR ASST DEV” is reported if the RFC is not locked when transitioning to Lightoff.
450017-001 Rev A (February 2003) Page 1 of 3 SB0052
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Image | Model C30 Software Version 4.93 Release Notes
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: firstname.lastname@example.org