Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Model C30 Software Version 5.02 Release Notes
Original File Name Searched: SB0066_C30_Software_V5.02.pdf | Google It | Yahoo | Bing
Text | Model C30 Software Version 5.02 Release Notes | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Facsimile: (818) 734-5320 • Website: www.microturbine.com
Service Bulletin SB0066
Date: From: Subject:
All Capstone Model C30 Stationary MicroTurbine systems described as follows:
• Model C30 MicroTurbines with version 5.01 experiencing a 5011 Frame EEProm Write warning may be upgraded to version 5.02 during a scheduled visit.
• Model C30 MicroTurbines with version 4.93 software (see SB0052) may be upgraded to version 5.02 during a scheduled visit – upgrading is recommended.
• Model C30 MicroTurbines with versions 4.95, 4.96, 4.98, and 4.99 software deviations MUST be upgraded to version 5.02 software.
Version 5.02 software replaces versions 5.01, 4.93, 4.95, 4.96, 4.98, and 4.99, and incorporates all related changes from these versions. Version 5.02 is released to support all Model C30 Stationary MicroTurbine systems. Major improvements for the version 5.02 and for the various software versions incorporated in version 5.02 are as follows:
Version 5.02 Updates
1. Updates to SPI Communication to ensure memory (RAM and EEProm) are locked so that multiple tasks can read/write to memory without overwriting each other.
Version 5.01 Updates
1. Modified engine and frame PM read/write algorithm to overcome PM checksum faults (5004, 5012) observed in the field.
2. Fixed inaccurate Battery SOC charge. This was reported by customers not being able to accurately gauge battery health after extended storage.
3. Fixed Auto Restart disable for MultiPac systems. Required a matching change in PowerServer code. For applications using a PowerServer, this feature requires CPS software version 2.20 or later.
4. Auto-Restart Delay is now ignored when a manual start is initiated with Auto-Restart set to NO.
450043-001 Rev B (June 2004) Page 1 of 5
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Capstone Technical Support
Model C30 Software Version 5.02 Release Notes
Image | Model C30 Software Version 5.02 Release Notes
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: email@example.com