Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Model C60 v4.50 Software Release
Original File Name Searched: SB0078_C60_v4.50_Software_Release.pdf | Google It | Yahoo | Bing
Text | Model C60 v4.50 Software Release | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Facsimile: (818) 734-5320 • Website: www.microturbine.com
Service Bulletin SB0078
Date: From: Subject:
Capstone Technical Support Model C60 v4.50 Software Release
All Capstone Model C60 MicroTurbine systems, including Industrial and ICHP systems.
Improvements incorporated in Model C60 software version 4.50 are summarized as follows:
1. Incorporated software compatibility for the Woodward Valve Controller (UFCB) with existing engine components.
2. Added generator power on the first line of the display panel menu selection. The second line adds “OK” or FLT status before the turbine number. If no fault is present, “OK” will appear. If any fault with severity level greater than “1” is present, “FLT” will display:
System Data 1/13
GC Single OK(/FLT) 1 xx.x kW Gen
xx.x kW Out
3. Incorporated Dual Mode Fast Transfer capability, which enables the system to fast transfer between Stand Alone (SA) and Grid Connect (GC) operation without shutting down using Dual Mode operation with the DMC connected (see Capstone Fast Transfer Application Guide 480011) for additional details.
a. Transfer from GC to SA operation is conducted automatically after the detection of the loss of the grid.
b. Transfer from SA to GC operation depends on the following system settings:
i. When the system is running in SA Load state, recovery of the grid will make the system transfer to SA recharge state after a one minute forced SA load operation.
ii. If GC Enable mode is set as AUTO, the system starts to check the grid reconnection condition after entering SA Recharge state. The grid must be in good condition for at least of five minutes before the system can transfer from SA Recharge state to GC Load state.
iii. If the system’s GC Enable mode is set as MANUAL, the system will stay in SA Recharge state and a new user Start command is required to start the system in GC operation. If the system does not receive a user Start command within two hours, the system will transfer from SA recharge to SA Cooldown state.
450063-001 Rev A (November 2005) Page 1 of 3
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Image | Model C60 v4.50 Software Release
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: firstname.lastname@example.org