Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | PM Programming of LCM and BCM Control Boards
Original File Name Searched: SN0009_PM_Programming_of_LCM_BCM_CB.pdf | Google It | Yahoo | Bing
Text | PM Programming of LCM and BCM Control Boards | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Facsimile: (818) 734-5320 • Website: www.microturbine.com
Service Notice SN0009
Date: From: Subject:
Model C60 installations configured with the Stand Alone option.
Capstone has identified that the current CRMS PM Write drop down menu for the BCM Control Board does not allow selection of new board (P/N 511711-101). This inability to electronically display the current configuration does not hinder MicroTurbine operation or cause the system to malfunction. However, failure to correctly identify the new board may cause traceability issues if BCM service is later required.
Historically, PM programming was performed at the LCM and BCM assembly level and device selections were available only for the LCM, LCM_CB and BCM. This was because the previous Control Board (P/N 511710-100) was used in both the LCM and BCM assemblies. As such, the PM Programmer software provided only a LCM_CB drop down selection. Version 2.09 of the PM Programmer expands the programming capabilities of the PM Write menu to allow a BCM_CB selection (see Figure 1).
CRMS version 4.41 (or later) is required to enable the programming of the BCM_CB properly. Both the CRMS software version 4.41 and the PM Programmer version 2.09 are available from the Member’s Only website. Refer to the CRMS Maintenance Edition Technical Reference Chapter 8: “PM Uploading” document for further details on the PM Write functionality of CRMS.
The new procedure for programming a BCM or LCM Assembly and/or Control Board is as follows:
Programming of a BCM:
• Program the BCM (Assy P/N and S/N found on the BCM packaging)
• Program the BCM_CB (Assy P/N and S/N found on the barcode label of the Control Board inside the BCM).
Programming of an LCM:
• Program the LCM (Assy P/N and S/N found on the LCM packaging)
• Program the LCM_CB (Assy P/N and S/N found on the barcode label of the Control Board inside the LCM).
450041-001 Rev A (June 2004) Page 1 of 2
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Capstone Technical Support
PM Programming of LCM and BCM Control Boards
Image | PM Programming of LCM and BCM Control Boards
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: firstname.lastname@example.org