Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Shutdown Command
Original File Name Searched: sb0001.pdf | Google It | Yahoo | Bing
Text | Shutdown Command | 001
All “Charlie” units with version 2.0 or earlier control software.
In grid-parallel mode, if you issue a “Power Disable” command, followed by a “Stop” command, the unit will fault and shut down, usually without the cooldown cycle. The fault will usually be “FAST BUS OVERVOLTS”, or “UNDERSPEED”, or “OVERSPEED”.
This is caused by a problem in the control software up to and including version 2.0. You can determine the control software version in your unit via the “Configuration” menu on your control panel. It will be on the menu line “LCI CODE X.X[.X.X]” Note that this is not the BOOT software version, which is also available via the same menu..
The next software release will eliminate this condition. . Until then, when you shut down your turbogenerator, use the “Stop” command only. The software will automatically disable the power output and then shut down normally. The “Power Disable” command should not be used.
SERVICE BULLETIN 97SBR0001 April, 1997
This information is confidential and proprietary to Capstone. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered.
Image | Shutdown Command
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: firstname.lastname@example.org