Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | SSR Transient Voltage Suppressor Installation Instructions
Original File Name Searched: SB0015_SSR_Transient_Voltage_Suppressor.pdf | Google It | Yahoo | Bing
Text | SSR Transient Voltage Suppressor Installation Instructions | 001
Date: From: Subject:
June 2001 (Updated from January 2001)
Capstone Customer Service
SSR Transient Voltage Suppressor Installation Instructions
Capstone Customer Service Toll Free Phone: (877) 282-8966 E-mail: email@example.com Phone: (818) 734-5325 ■ Fax: (818) 734-5358
Be sure to read and comply with the instructions contained within this Service Bulletin prior to installing transient voltage suppressors.
This Service Bulletin describes the addition of transient voltage (or contact) suppressors whenever the Solid State Relay (SSR) output in the User Connection Bay Extended (UCBE or UCBEE) is connected to an external circuit containing relay coils, contactor coils, or motors.
These transient voltage suppressors are necessary and essential REGARDLESS of the voltage level at the device connected to the SSR output.
Notice that the SSR outputs are limited to 100 milliamps on AC circuits and to 50 milliamps on DC circuits.
All Capstone MicroTurbine installations that use the SSR outputs for various functions are affected.
512100-002 (June 2001) Page 1 of 4 Service Bulletin SB0015.
This information is confidential and proprietary to Capstone. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered.
Image | SSR Transient Voltage Suppressor Installation Instructions
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: firstname.lastname@example.org