Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Technical Reference MultiPac Operation Technical Information
Original File Name Searched: 410032E_MultiPac_Operation_TR.pdf | Google It | Yahoo | Bing
Text | Technical Reference MultiPac Operation Technical Information | 001
Technical Reference MultiPac Operation Technical Information
This document provides technical information for operating Capstone Model C30 and Model C60/C65 MicroTurbines in a collective arrangement known as a MultiPac. In a MultiPac, MicroTurbines can be installed in groups of up to 20 units (100 units with the optional Capstone PowerServer) to operate as a single power generation source. Refer to the Capstone PowerServer Technical Reference (410024) for details utilizing a PowerServer in MultiPac installations.
MultiPac operation features synchronous voltage and frequency for all MicroTurbines in the group. Individual turbines share power and load on both a dynamic and steady state basis. A single physical and logical control point, designated as the “master”, directs signal and command information to all other turbines. However, any individual turbine in the group may be designated as the master.
MultiPac can be operated in any of three available modes: Stand Alone, Grid Connect or Dual Mode. In each mode, individual MicroTurbines share power, current and load on both a dynamic and steady state basis, and generate current to meet the required load demand. Dual Mode operation requires purchase of an optional Capstone Dual Mode Controller.
All Capstone MicroTurbines are capable of operating in a MultiPac. A MultiPac Interconnection Kit (509949) is required to implement MultiPac functionality. The kit includes an inter-controller cable, two inter-controller terminators, a coaxial cable, and two coaxial terminations. Contact Capstone Technical Support for order information.
An illustrative interconnection diagram is presented in Figure 1.
Point of Common Connection
Capstone Turbine Corporation 21211 Nordhoff Street Chatsworth CA 91311 USA Telephone: (818) 734-5300 Facsimile: (818) 734-5320 Website: www.microturbine.com
Figure 1. Typical MultiPac Interconnection
410032 Rev E (October 2009)
Page 1 of 16
Capstone reserves the right to change or modify, without notice, the design, specifications, and/or contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Image | Technical Reference MultiPac Operation Technical Information
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: email@example.com