Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | TET themocouple Replacement Capstone Model 330 Micro Turbine
Original File Name Searched: SB0034_TET_Thermocouple_Replacement_C30.pdf | Google It | Yahoo | Bing
Text | TET themocouple Replacement Capstone Model 330 Micro Turbine | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Facsimile: (818) 734-5320 • Website: www.microturbine.com
Date: From: Subject:
All Model 330 MicroTurbine systems shipped between April 1999 and June 2001 that use the TET Thermocouple 508625-100 for replacement. The thermocouple Part Number is identified on the label attached to the thermocouple cable.
On a number of TET Thermocouples 508625-100 shipped for standard maintenance, the -inch nut on the thermocouple is not placed at the proper position. This will result in incorrect positioning of the sensor inside the engine, leading to frequent occurrence of Fault Codes 6009 (Overtemperature), 6010 (High Overtemperature), and 6012 (Engine Flameout). Any of these conditions may potentially lead to engine overtemperature damage or flame instability. To eliminate these problems, it is imperative to set the -inch nut on the thermocouple at approximately 140 mm (5 inches) from the tip of the thermocouple.
If the MicroTurbine experiences the above-mentioned conditions after replacing the TET Thermocouple 508625-100, refer to Work Instructions 513576 for proper thermocouple adjustment procedures.
Also, if you are replacing the TET Thermocouple 508625-100, refer to Work Instructions 513576 for proper thermocouple replacement procedures.
If you have additional questions, please contact: Capstone Technical Support
Capstone Technical Support
TET Thermocouple Replacement Capstone Model 330 MicroTurbine
On currently shipped TET Thermocouples 508625-100, the locking ferrule for the -inch nut is pre-swaged onto the thermocouple, allowing the sensor to be positioned correctly inside the engine.
Toll Free Telephone:
(818) 407-3600 (818) 734-1080 (877) 282-8966
513577-001 Rev A (Feb 2002) Page 1 of 1 SB0034
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the equipment specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Image | TET themocouple Replacement Capstone Model 330 Micro Turbine
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: firstname.lastname@example.org