Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | UCB Board Replacement - Model C60 MicroTurbine
Original File Name Searched: SN0008_C60_UCB_Board_Replacement.pdf | Google It | Yahoo | Bing
Text | UCB Board Replacement - Model C60 MicroTurbine | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Facsimile: (818) 734-5320 • Website: www.microturbine.com
Service Notice SN0008
Date: From: Subject:
Capstone Technical Support
UCB Board Replacement - Model C60 MicroTurbine
All Capstone Model C60 MicroTurbine systems with Serial Numbers listed below:
UCB boards shipped as spares between December 10, 2003 and March 8, 2004, are also affected and should be replaced.
Only Capstone Authorized Serviced Providers (ASP’s) should open the MicroTurbine and other equipment connected to the MicroTurbine. The systems can include multiple sources of power. Observe and adhere to the Safety Instructions contained within the MicroTurbine User’s Manual.
It has been found that the UCB board (511714-102) shipped with the Model C60 MicroTurbine systems listed above does not have the correct firmware programming, and should be replaced. In addition, the UCB boards shipped as spares between December 10, 2003 and March 8, 2004, may have incorrect firmware programming, and should be replaced.
For systems listed above, Capstone requests that at the next scheduled service visit, the ASP should check the UCB software version using the display panel or the CRMS. If the version code reads V2.00, it is incorrect (the correct version is V2.01 or higher), and the UCB board should be replaced with a new board. Refer to UCB Replacement Work Instructions (440049) for installation details.
450040-001 Rev A (April 2004) Page 1 of 2
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Although the label on the UCB firmware may show the correct software version, V2.01 or higher, it is necessary to verify the software version using the display panel or the CRMS.
Image | UCB Board Replacement - Model C60 MicroTurbine
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: email@example.com