Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | UNIGIN Service Bulletin heat recovery unit users
Original File Name Searched: UnifinSB10.pdf | Google It | Yahoo | Bing
Text | UNIGIN Service Bulletin heat recovery unit users | 001
1030 Clarke Side Road • Box 5395 • Station B • London, ON Canada N6A 4P4 email@example.com
SERVICE BULLETIN 10 (Rev. 1) DATE: April 14, 2003 R0 (Rev. 1 June 6/03)
TO: micoGenTM Heat Recovery Unit Users
Contact: Tim Ryan, Customer Service Leader
RE: Control Board Overheating
From: L. Brescacin,
Manager, Engineering & Product Development
PHONE: (519) 451-0310 Ext 222 FAX: (519) 451-0310
This bulletin is applicable only to First-generation micoGenTM units with manufacturing dates prior to Nov. 2000. In some cases the insulation of the bottom internal portion of the heat recovery unit may have come off causing excessive heat to be discharged into the enclosure. In other cases insulation may have been insufficient or may have come off of the back of the covering of the control board. The result in both cases can be over-heating of the control board.
Unifin addressed this problem in all known cases by either travelling to sites which had units that were affected or by sending kits to the owners of such units with instructions for installing this insulation.
If you have a unit from this era with control board failure due to overheating, contact Unifin Customer Service for procedures that instruct how to replace control boards and how and where to install required insulation to protect against control board overheating.
Note: Serial numbers affected begin with a 9 or a 0.
Reference Kit: MG-KIT-SB10 Procedure MES-MG-004
Image | UNIGIN Service Bulletin heat recovery unit users
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: firstname.lastname@example.org