Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Wiring Interlock between Multiple MicroTurbines with Common Exhaust Duct
Original File Name Searched: SB0046_Wiring_Interlock_Between_MicroTurbines_with_Common_Duct.pdf | Google It | Yahoo | Bing
Text | Wiring Interlock between Multiple MicroTurbines with Common Exhaust Duct | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Telephone: (818) 734-5300 • Facsimile: (818) 734-5320 • Website: www.microturbine.com
Service Bulletin SB0046
Date: From: Subject:
Capstone Technical Support
Wiring Interlock between Multiple MicroTurbines with Common Exhaust Duct
All Capstone Turbine Corporation® Model C30 and C60 MicroTurbine systems operating with a common exhaust duct including systems with back flow dampers.
Only Capstone Authorized Serviced Providers (ASP’s) should open the MicroTurbine and other equipment connected to the MicroTurbine. The systems can include multiple sources of power. The fuel used by the MicroTurbine is flammable and explosive. Keep flames, cigarettes, sparks, and electrical arc-producing equipment away from the MicroTurbine. Observe and adhere to the Safety Instructions contained within the MicroTurbine documentation.
Description of Problem
This service bulletin is intended to notify Authorized Service Providers of a possible safety issue/fire hazard or component failure relating to MicroTurbine systems sharing a common exhaust duct.
The back flow damper on two or more MicroTurbine systems sharing a common exhaust duct may warp after exposure to heat. This damper failure may affect the seal that prevents exhaust back flow and cause hot exhaust from an operating MicroTurbine unit to flow backwards through a non-operating MicroTurbine unit.
Reverse flow of hot exhaust may cause overheating of the generator and engine inlet components, resulting in damage to those components. In addition, damage to the non- operating MicroTurbine can result during a start of another unit due to backpressure on the engine’s rotating components.
All MicroTurbines on a common duct must run simultaneously at the same power level. In addition, Capstone requires a wiring interlock mechanism to be installed between MicroTurbine systems.
450011-001 Rev A (December 2002) Page 1 of 4
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Image | Wiring Interlock between Multiple MicroTurbines with Common Exhaust Duct
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: firstname.lastname@example.org