Microturbine Search Engine Series
Capstone Turbine Publications search was updated real-time via Filemaker on:Capstone Turbine Publications | Return to Search List
Search Completed | Title | Work Instructions Smart Proportional Valve (SPV25) Replacement Capstone Model C60 MicroTurbine
Original File Name Searched: 440028_SPV.pdf | Google It | Yahoo | Bing
Text | Work Instructions Smart Proportional Valve (SPV25) Replacement Capstone Model C60 MicroTurbine | 001
Capstone Turbine Corporation • 21211 Nordhoff Street • Chatsworth • CA 91311 • USA Phone: (818) 734-5300 • Fax: (818) 734-5320 • Web: www.microturbine.com
Smart Proportional Valve (SPV25) Replacement Capstone Model C60 MicroTurbine
Purpose and Scope
This document describes the procedure for replacing the Smart Proportional Valve (SPV25) on the Capstone Model C60 MicroTurbine.
This document presents information sufficient to allow an Authorized Service Provider (ASP) to properly replace the SPV25.
Conduct maintenance in a clean, well-lighted area using normal shop tooling to avoid damage to delicate components.
Retain all parts removed for use at assembly, unless otherwise specified. Discard all parts as noted in this document.
Only Capstone Authorized Service Providers (ASP’s) should open the MicroTurbine and other equipment connected to the MicroTurbine. The systems can include multiple sources of power.
Observe and adhere to the Safety Precautions listed below when servicing your MicroTurbine. Read and become familiar with the General Safety Precautions and Instructions contained within the MicroTurbine System Manual. Before servicing:
Check to ensure that the inlet fuel supply is SHUT OFF
Always check to ensure that your MicroTurbine is de-energized from
the utility. Isolate and lock out the utility (if applicable).
Isolate and lock out any other sources of power to the MicroTurbine. For example, connections to the solid state relays in the MicroTurbine Communications Bay.
Open the Stand Alone battery circuit breaker, lock it in the OFF position, and then unplug the battery cable.
Wait at least five minutes after disconnection from utility before servicing to allow for electrical energy dissipation.
Verify that no voltage is present on any electrical terminals.
Never work on energized equipment.
Observe all safety precautions to prevent Injury or death.
440028-001 Rev A (December 2002) Page 1 of 2
This information is proprietary to Capstone Turbine Corporation. Neither this document nor the information contained herein shall be copied, disclosed to others, or used for any purposes other than the specific purpose for which this document was delivered. Capstone reserves the right to change or modify without notice, the design, the product specifications, and/or the contents of this document without incurring any obligation either with respect to equipment previously sold or in the process of construction.
Image | Work Instructions Smart Proportional Valve (SPV25) Replacement Capstone Model C60 MicroTurbine
|Capstone Turbine For Sale - Microturbine C30 C65 C200 C600 C800 C1000 - Go to microturbine website|
Search Engine Contact: email@example.com